Storage tank safety tests underestimate pathogen levels - study
Deadly bacteria lurking in drinking water storage tanks could be missed by standard health and safety tests, scientists have warned in a new report.
Cold water storage tanks supplying public drinking water are regularly checked for harmful pathogenic bacteria such as Legionnaires' disease and E.coli.
However, microbiological analysis by researchers from Brunel University London found that samples taken as standard from the top of the tank are 40 per cent less likely to raise a red flag than samples taken from the opposite end.
One in five samples taken from the top of the tank did not trigger the urgent safety action that samples from the bottom of the same tank showed was needed.
"These results call into question the reliability of present measures used to protect the public from waterborne pathogenic diseases, including Legionella," said Aji Peter, a PhD student from Brunel’s Institute of Environment, Health and Societies, who carried out the research.
Cold water storage tanks are often found on the roofs or in the basements of public buildings such as schools and hospitals, and can be a source of repeated bacterial contamination.
Current safety regulations require a sample of water be taken from under the ball valve at the top of the tank for regular microbiological monitoring, although scientists are now calling for the standard safety tests to be changed to look at samples taken from the far end of the tank, where water is likely to be warmer and hold more bacteria-feeding sediment.
"Given the disparity between measurements taken at different ends of the tanks, monitoring at the far end would provide a much more accurate indication of microbiological contamination," Peter said.
"This would allow appropriate precautions to be taken to protect the public from waterborne pathogenic diseases, including Legionnaires’ disease."
The report can be viewed here.
- MP pushes UU for transparency over 'crypto' contamination South Ribble MP Seema Kennedy is pushing United Utilities (UU) 'for a greater degree of transparency' over the... Read More >
- Welsh Water reaches another safety milestone The Costain team working on the Welsh Water Framework on 248 different projects has achieved over 3 million man hours... Read More >
- Upgrade for Severn Trent laboratory in Bridgend The First Minister of Wales Carwyn Jones officially reopened Severn Trent's laboratories in Bridgend on Friday (October... Read More >
- Shifting the dial on drinking water challenges Ahead of WWT Drinking Water Quality Conference, Anglian Water's director of water services, Paul Valleley, provides the... Read More >
- Over-pressurisation: A serious risk for lime storage silos Hycontrol managing director Nigel Allen warns that many lime storage silos are disasters waiting to happen, and steps need... Read More >
- Why valve checks are an essential part of summer maintenance Fraser Higgins, Durapipe UK industrial product manager, explains why valves should not be overlooked as part of the summer... Read More >
- Case Study: Pumping up quality at Burnham Jetty A year's worth of planning, seamless collaboration and technical expertise were crucial to the success of a complex... Read More >
- Lead Pipe Removal: Taking the Lead Lead pipes represent a proven risk to water quality and people's health - but 50 years after they were banned for new use,... Read More >