South West Water has to pay £205K for Fal sewage spill
South West Water (SWW) has been ordered to pay £205,000 in fines and costs for sewage spill that forced mussel and oyster beds to close in the Fal estuary in Cornwall.
On August 26, 2013, untreated sewage overflowed from the water company’s Newham sewage treatment works near Truro into the Fal, an internationally important shellfishery, Site of Special Scientific Interest (SSSI) and Special Area of Conservation (SAC).
The illegal spill occurred after a piece of redundant grating fell and partially blocked an inlet at the works, causing sewage to back up and overflow into the estuary via a storm storage outfall. The spill continued for about 9.5 hours, during which time enough sewage escaped to fill 4,563 bath tubs (730,000 litres).
The discharge occurred close to mussel and oyster beds at Malpas and Grimes Bar. As a precaution, these shellfisheries were temporarily closed by Cornwall Port Health Authority because of the possible risk of contamination by harmful viruses and bacteria such as Norovirus and e.coli.
The decision to close the shellfish beds was taken just before the start of the commercial harvesting season (October 1). Although most harvesting is done during the commercial season, there is a risk small quantities of shellfish may be hand-picked by individuals outside of this time and there would have been a potential risk to those consumers.
Sewage at the Newham treatment works normally undergoes a high level of treatment (tertiary) including ultraviolet (UV) that kills bacteria and disinfects effluent. The UV disinfection system is required at this site because of the Fal estuary’s designation as a shellfishery.
The sewage discharged over a bank holiday on August 26 was settled and screened, but otherwise untreated and occurred outside of a storm event. This would have resulted in a significant increase in levels of bacteria in parts of the Fal estuary and meant the treatment works was in breach of its Environment Agency permit.
Mark Pilcher, team leader for the Environment Agency in west Cornwall, said: “It is essential large sewage works bordering estuaries with conservation designations and also containing shellfish beds are operated and inspected to a high standard to prevent unpermitted sewage spills posing risks to public health and the environment. In this case an inspection programme or removal of a redundant grating structure would have removed the risk of this grating falling into the sewage works and blocking it leading to the spill of sewage.”
SWW was fined £185,000 plus £20,000 costs after pleading guilty to two offences under the Environmental Permitting Regulations 2010 including, on August 26, 2013, causing pollution of the Fal estuary through the illegal discharge of sewage and failing to maintain a saline tank valve at its Newham sewage treatment works. The company was fined £175,000 for the first offence and £10,000 for the second.
The case, brought by the Environment Agency, was heard at Truro Crown Court on February 15, 2017.
- Water theft could lead to prosecution, warns South West Water South West Water (SWW) has warned customers not to steal water from its public supply network or they could run the risk... Read More >
- Sewage sludge makes concrete, say Malaysian researchers Dried sewage sludge could be an alternative cement material for concrete, researchers in Malaysia have found. Read More >
- Water HQ switches to sunshine South West Water (SWW) has completed the installation of solar panels on the roof of its Exeter headquarters. The work to... Read More >
- River rescue: High-resolution monitoring of nutrient pollution OTT Hydrometry's Nigel Grimsley discusses the technologies that have overcome traditional barriers to the continuous... Read More >
- Opinion: Phosphorus just one of the problem pollutants Phosphorus may be front of mind for wastewater treatment in the UK at the moment, but this emphasis should not mean that... Read More >
- Top Tips for... turbidity monitoring The impact that high levels of turbidity and suspended solids can have on the aquatic environment makes it a particularly... Read More >
- "Farmers want to be part of the solution" on catchment management Emma Goddard, Head of Environment, South East Water, speaks to WWT about the company's award-winning catchment management... Read More >
- Catchment management: Seeking Solutions at Source After Winterton Water Treatment Works spent almost six years out of operation due to pesticide problems, Anglian Water... Read More >