Severn Trent cautioned for supplying water 'unfit for human consumption'
Severn Trent Water has been cautioned by the Drinking Water Inspectorate (DWI) for supplying water that was 'unfit for human consumption'.
The caution relates to an event in March 2016 when consumers in 3,700 properties were advised by Severn Trent not to use their water for 26 hours due to elevated levels of chlorine.
The event occurred at Castle Donington Service Reservoir, Derbyshire, and involved the contents of a sodium hypochlorite storage tank draining into the inlet main to the service reservoir. The DWI’s investigation has concluded that this serious event “was avoidable, and that there were a number of missed opportunities to identify and rectify the problem before the event”.
Severn Trent, which admitted supplying water unfit for human consumption under Section 70 of the Water Industry Act (1991), isolated the chlorine dosing equipment at the service reservoir, and flushed the supply network to remove the affected water. However, the incident resulted in the supply of unwholesome water to some consumers, some of whom rejected the water supplied to them.
The company has replaced the chlorine dosing equipment at the service reservoir site to prevent a recurrence of the event. It has also audited more than 190 similar secondary chlorine dosing rigs currently operational across its asset base, and has instigated corrective actions as necessary.
Other actions taken to further mitigate the risk of a similar event occurring at other sites include a competency assessment of all staff involved in operational activities at service reservoirs and at chlorine booster stations; a review of chlorine booster station alarm settings and telemetry stations for reliability; changes in procedures; a review of the use of GIS systems to more accurately and rapidly identify areas affected in any future event scenario; and a review of alternative supply management arrangements.
- Sarah Bentley confirmed as new Thames Water CEO Bentley joins Thames from Severn Trent Read More >
- Severn Trent reveals £1.2bn environmental plans Severn Trent has revealed plans to spend £1.2 billion to improve the environment, help sustainability and support... Read More >
- Severn Trent begins work on £15m environmental programme Severn Trent has started work on a £15 million environmental programme that is set to bring benefits to the region's fish... Read More >
- Asset resilience will be one of the beneficiaries of PR19 Richard Broome, Managing Director at LSBUD talks about why Ofwat's PR19 could prove to be such a positive influence on... Read More >
- Reaching net carbon zero In summer 2019, the water industry committed to reach net carbon zero by 2030. This is a very ambitious aim and... Read More >
- Meeting AMP7 leakage targets Damian Crawford, head of smart networks & leakage at Stantec, discusses how becoming data-rich and knowledge-smart can... Read More >
- Rewarding excellence WWT content director Alec Peachey looks ahead to next year's Water Industry Awards. Read More >
- Delivering a smart network Tom Mills, senior director UK&I at Sensus, examines what a smart water network really means - and how to get there. Read More >