Anglian Water takes an EU for sewage pollution
The Environment Agency (EA) has announced that an enforcement undertaking (EU) has been agreed with Anglian Water after the utility polluted Houghton Brook, Cambridgeshire with sewage.
Around 150 fish died when sewage from Ilex Road Pumping Station in St Ives was pumped into the water system for ten hours via the emergency overflow. The overflow was mainly caused by excessive levels of un-flushable material/rag blocking the pump, which was a known issue at the works.
Contributing factors included a second pump being out of service during the incident and the failure of an alarm.
At the time of the pollution, Anglian Water tankered the watercourse to prevent pollution travelling further downstream and two days later the stream was running clear.
Anglian Water has since replaced equipment at the pumping station including a pump that can better cope with high levels of rag.
The EA accepted the offer by the water company to put right any damage caused by the pollution and to donate to an environmental charity.
As part of the EU, Anglian Water has donated £100,000 to the Wildlife Trust for Bedfordshire, Cambridgeshire and Northamptonshire to benefit the local environment and also paid the EA’s costs.
Jeremy Hay, EA officer, said: “Enforcement undertakings allow those who commit offences to restore the environment and to take steps to prevent a recurrence. When appropriate, they allow a quicker resolution than a prosecution and help offenders who are prepared to take responsibility for their actions to put things right voluntarily working with their local communities.”
Formal sample results taken after the incident in September 2014 showed that sewage had polluted approximately 635m of the stream.
The EU was offered in relation to an offence of pollution under section 4 of the Salmon and Freshwater Fisheries Act 1975. It was accepted in March 2017 and the undertaking was completed on May 30, 2017.
- Northumbrian Water fined for pollution incidents Northumbrian Water has been ordered to pay over £33,600 in fines and costs for three separate pollution incidents,... Read More >
- M and N Electrical wins expanded Anglian Water contract M&N Electrical & Mechanical Services is set to expand its remit with Anglian Water following confirmation that the... Read More >
- Brick manufacturer fined £33K for brook pollution A Staffordshire firm has been fined £27,000 and ordered to pay more than £6,500 in costs after admitting polluting a brook... Read More >
- Drinking Water Quality conference to highlight regulatory standards Water company directors, chief scientists and water quality experts are set to gather on November 8th to discuss the... Read More >
- New trends and technologies under spotlight at WWEM 2018 Over 80 seminars will take place over the course of two days at WWEM 2018, the water, wastewater & environmental... Read More >
- River rescue: High-resolution monitoring of nutrient pollution OTT Hydrometry's Nigel Grimsley discusses the technologies that have overcome traditional barriers to the continuous... Read More >
- Opinion: Phosphorus just one of the problem pollutants Phosphorus may be front of mind for wastewater treatment in the UK at the moment, but this emphasis should not mean that... Read More >
- Top Tips for... turbidity monitoring The impact that high levels of turbidity and suspended solids can have on the aquatic environment makes it a particularly... Read More >