Anglian Water fined following pollution incident
Anglian Water has been ordered to pay more than £156,000 for polluting a Northamptonshire brook with sewage, following an incident in 2016.
In a prosecution brought by the Environment Agency, Leicester Magistrates’ Court fined the utility company £146,000 and ordered them to pay £10,676 in costs after it found the company’s negligence and lack of maintenance were behind a number of failures at the Yardley Hastings sewage plant.
The incident occurred over two days in August 2016, when at least a kilometre and a half of Grendon Brook was contaminated with sewage.
In mitigation, the court heard that Anglian Water reported the pollution itself and cooperated with the investigation.
The company has since taken steps to fix the faults and to clean up the brook.
The pollution was caused by various failures at the pumping station, which takes in raw sewage and transfers it to the main site for treatment.
The pumps became air-locked and stopped working, causing sewage to back up in the storage tank, which filled and discharged into the nearby brook.
Alarms which should have alerted staff to the problem also failed to sound.
Investigations found the faults were due to a lack of maintenance – and although Anglian Water had undertaken three maintenance visits, they had no records of the affected parts being cleaned or maintained in the year leading up to the incident.
The pollution was reported on 24 August but was not acted on, and the company had no record of the report being made.
An alarm triggered the same day to indicate a problem as there was no flow from the pumping station to the main sewage works, but this was mistakenly closed down without being resolved.
The pollution continued intermittently for two days until it was noticed and stopped on 26 August – but this could have been done sooner if earlier reports had been acted on.
Anglian Water pleaded guilty to breaching the Environmental Permitting (England and Wales) Regulations 2010 and the Water Resources Act 1991 in the case heard on 12 September.
“Earlier this year, we pledged a tougher approach towards water companies that don’t live up to their environmental responsibilities, and this case proves that we will hold them to account when they pollute the natural environment,” said the senior environment officer with the Environment Agency who investigated the incident, Adam Glassford.
“It’s our job as a regulator to protect people and wildlife, and we will take action when they’re put at risk.”
- Anglian Water security manager awarded MBE Anglian Water's security manager, Lynda Chamberlain, who recently retired, has been awarded an MBE in the Queen's birthday... Read More >
- EA seeks reassurance over companies' water quality control The Environment Agency (EA) is asking the water and sewerage companies for reassurance that they have plans to bring water... Read More >
- New nitrate removal plant for Anglian Water's Retford WTW Water and wastewater solutions provider ACWA Services has been contracted to design and build a new state-of-the-art... Read More >
- Through the keyhole: The King's Scholars' Pond project The use of keyhole engineering on Thames Water's King's Scholars' Pond project saved money and carbon while keeping London... Read More >
- Flushed with success: FOG and Unflushables Southern Water's FOG and Unflushables programme has brought a significant improvement in the state of its sewers. Robin... Read More >
- Will SfA8 make as big a splash as hoped? Martin Lambley, product manager for stormwater management at Wavin, looks at whether Sewers for Adoption 8 will meet... Read More >
- Developing ideas: Thames Water's innovative sewer plan Thames Water is radically re-engineering an Oxfordshire market town's sewer network to help developers prepare for... Read More >
- Brexit, WWII, ancient artefacts: Southern Water's testing sewer project Southern Water's £2.5 million project to replace an 800m stretch of sewer main in Kent was complicated by - among other... Read More >