Under pressure: Tackling leakage in new networks
Leakage in new pipelines represents a significant problem but, working alongside Scottish Water, Ant Hire Solutions has developed a new system that could help eliminate the issue
By Robin Hackett
With the battle against leakage largely focused on ageing pipes, problems with new networks can get overlooked.
Pipeline specialist Ant Hire Solutions recently carried out research that hints at the scale of the issue: 16 per cent of the new pipelines it tested over the course of a year were identified as leaking.
“Although the big problem with leakage is with existing networks, there’s also a lot of investment in new networks,” Ant Hire Solutions managing director Adrian Thompson says. “If they don’t start their 30- to 40-year life leak-free, we’re not going to meet the long-term targets. It’s a small piece of the leakage puzzle, but it’s a very important one.”
If the problem is to be eradicated, it’s essential that new pipelines are compliant with the IGN on pressure testing.
However, ensuring 100 per cent compliance has proved challenging – not only does it rely on contractors submitting accurate information to validate their work, it also requires the water company to correctly verify that data.
To simplify the process, Ant Hire has developed PIPE, a new end-to-end pressure-testing data management system and dashboard that provides a single view of pressure test performance, air content levels and leakage data in real time.
In addition to delivering instant feedback on whether a pipe has passed or failed, it helps water companies determine whether the testing process has been carried out correctly, with all the necessary information – including images from the worksite – accessible from a single dashboard.
The system was created with input from Scottish Water, which – despite comfortably meeting its leakage targets – had been seeing problems with failures in new assets.
“We had staff members who hadn’t been correctly trained and were accepting any contractors’ submissions on pressure-testing data,” Willie Langan, project manager at Scottish Water, says.
In search of a solution, Langan attended a training course to improve his understanding of pressure testing and, after seeing Ant Hire’s work in the field, began working with the company on ways to improve standards.
He has since provided input into the PIPE dashboard to make sure it meets water company needs, as well as translating the IGN document into layman’s terms so that all Scottish Water staff have the knowledge to ensure that, regardless of how contractors choose to submit pressure test information, new installations meet the required standards.
“If the contractors don’t do the test right, including supplying the geotagged photographic evidence, then we won’t accept it regardless of what the data is saying,” Langan says. “We need to see everything to ensure that test is 100 per cent fit for purpose for Scottish Water.”
All new mains installed in Scotland, regardless of the techniques used, are pressure tested accordingly.
The results of Ant Hire’s research demonstrate the clear need for improvements, with only 68 per cent of pipelines having passed its pressure tests first time.
The research also found that 11 per cent of new pipelines contained dangerous air content levels, which can lead to a sudden release of energy during the testing process when the air is compressed.
“If there’s any sign of excessive air we can stop the test because a lot of people don’t realise how dangerous that can be,” Thompson says. “You’re testing a pipe to see if there’s a failure and, if it does fail, it can be catastrophic.”
The hope is that, as well as identifying any faulty assets at the outset, holding contractors to higher standards will shine a spotlight on any areas for improvement in their working practices and, ultimately, lead to fewer failures in the future.
Tony Kitchen, head of pressure testing at Ant Hire, points out that PIPE not only flags up leaks in real time but, through data analysis, can also provide the likely cause of that leak.
“With polyethylene, for example, the majority of leakage is a result of joint failure and due to poor pipe preparation during the pipeline’s installation,” Kitchen says.
Thompson says contractors came around to the system’s advantages quickly after some initial doubts.
“The feedback we got from the contractors when they heard Scottish Water was going to put in the new testing regime was that they thought it was going to take longer and be more onerous,” he says.
“Actually, it’s much easier than it was previously because it’s all done instantaneously and they get the results right there and then.
“If the contractor follows what we say, they’ll get the job done right first time. We can demonstrate through the dashboard hours and hours of time saved through the process.”
While it is still early days, Langan says he is already seeing distinct improvements.
“We were accepting our contractors’ submissions without the correct knowledge and experience to actually prove or validate it as fit for purpose,” he says. “No longer will we accept substandard pipework. With the new testing regime, that’s eliminated a lot of the poor workmanship that’s been handed over.”
This article originally appeared in the July issue of WWT
- Rise of the 'wipe wash' clogs UK's drains and sewers A trend for using wet wipes to clean the body could be partly responsible for the repeated blockages which are the scourge... Read More >
- Comment: The vast potential of machine learning and data Recent efforts to use machine learning to predict bursts and leakage illustrate how the collaborative use of data could... Read More >
- Wessex Water gets to work on its biggest project so far Wessex Water is creating a water supply grid in order to meet supply demand for the next 25 years. The £225M project will... Read More >
- Time to get smart Mike Strahand, a director of the Sensors for Water Interest Group and MD at Analytical Technologies Inc., says the... Read More >
- Embracing the digital measurement revolution for wastewater Developments in digital sensing technology have opened up new possibilities for wastewater, Julian Edwards, analytical... Read More >
- Wessex Water's bustling Marketplace, three months on Neil Wilson, Wessex Water's director of risk and investment, says the company's new innovation platform is attracting... Read More >
- Developing ideas: Thames Water's innovative sewer plan Thames Water is radically re-engineering an Oxfordshire market town's sewer network to help developers prepare for... Read More >
- A glass half-full? Bringing water costs down for utility customers Mark Bullock, Balfour Beatty chief executive officer for rail and utilities, says the water sector must change its... Read More >