Measure for measure
Pump inefficiency and failure can be reduced by a range of measures, says Jeremy Salisbury of Brammer UK
Centrifugal process pumps often work in hostile and stressful operating conditions. Consequently, they can fail prematurely – resulting in lost productivity from unplanned downtime.
Improved reliability, reduced maintenance and lower energy consumption are all achievable by ensuring pumps operate at optimum speed and efficiency.
Cavitation is a significant cause of wear, especially in pumps required to start quickly.
When a liquid undergoes rapid pressure changes, cavities form in its lower pressure regions. When entering high pressure areas, these bubbles collapse, causing cyclic stressing and, ultimately, surface fatigue to the impeller, pump housing, or both.
Rapid pump stoppage – or failure – can also create significant problems. A sudden flow reduction can mean a valve closes rapidly, resulting in water hammer - a pressure surge or wave which can cause noise, vibration, blown valves, leaks, and even pipe collapse.
Meanwhile, vibration from component wear or misaligned and poorly balanced shafts can increase energy usage and maintenance costs, and even cause product failure.
Variable speed drives (VSDs) can reduce energy usage and help optimise reliability while closing the loop with regard to proportional–integral–derivative (PID) functionality. A VSD which reduces by 10% the speed of a 22kW pump operating 24 hours a day for 300 days annually can pay for itself through reduced energy usage in just eight months, depending on electricity costs. Energy is key, given that many pumps are specified larger than needed for the application. A small speed increase to up flow rate can potentially increase power demand significantly, meaning contingencies are successively built into the design process.
However, a VSD delivering a 4% speed decrease typically pays for itself in around two years through reduced energy costs. The only rider is that VSDs cannot be fitted to pumps operating under high head pressures.
This is because pressure varies in proportion to speed as per the pump affinity laws. In these cases, speed variation using any method is not advisable without due caution. Other options include v-belts, where potential issues like slippage have been largely circumvented by the latest synchronous belts, which do not require regular re-tensioning.
Meanwhile, the latest synchronous carbon belts offer far greater power-carrying capacity than was previously achievable, and exceptional flex fatigue resistance, meaning they bend more easily around pulleys and deliver a typical 5% energy efficiency advantage over v-belt drives.
For smaller pumps, a VSD is generally preferable, while soft start drive typically becomes economical for 22kW pumps or larger. However, there is a crossover area where either method is suitable depending on application requirements. For example, an application starting once per month and running at constant speed will require soft start, however a VSD will be more appropriate if demand from the pump varies. Overall performance can also be increased by fitting pressure sensors in applications with variable throughput. The sensor will feed back any reduced flow requirement to the VSD which will cause the motor to slow accordingly, delivering energy savings with no risk to the pump.
Ragging – or fouling of impellers – can significantly affect pump performance. It can cause partial or complete blockage, with problems of downtime extending over several days, as well as cleaning costs, with back-up systems placed under additional pressure and, in the worst cases, effluent leakage.
This can be negated by an intelligent pump control system which monitors overall performance, triggering an automated cleansing cycle if performance crosses pre-programmed ‘out of profile’ boundaries.
Identifying problems before they occur is integral to optimising efficiency and minimising downtime. Modern condition monitoring systems, such as sensors and accelerometers, monitor vibration levels and temperature changes with information downloadable to a hand-held system.
For remote or hard-to-access locations, information is fed into a central system which can provide warnings of unusual or undesirable readings, allowing planned maintenance if required. Modern software tools even suggest likely causes, and prescribed remedial actions, based on data provided.
Pumps should always operate on a stable baseplate with shafts optimally aligned and lubricated according to manufacturer instructions, otherwise poor performance and ultimately failure are almost inevitable. As with any other component, replacing parts without detailed investigation into the problem’s root cause will not re-establish optimum performance.
The following points should be checked monthly: priming speed, capacity, noise in the pump casing, gaskets and O-rings, shaft seal leakage of air and water; hose, hose washers and suction strainer. Six-monthly checks should be made of:
- Impeller wear
- Clearance between the impeller face and the volute
- Shaft seal and shaft sleeve wear
- Cleaning of casing and volute passages
This combination of regular checks and proactive maintenance, coupled with appropriate control methods, will contribute significantly towards optimising efficiency, minimising downtime and reducing whole
- Project Focus: Pumping station upgrade for Stillingfleet When the Ouse and Derwent Drainage Board decided to update Stillingfleet surface water pumping station, installing new... Read More >
- Ending the nightmare of wet-wipe pump blockages An ingenious device developed in partnership with Scottish Water promises to reduce wastewater pump maintenance by... Read More >
- Comment: Ease off the pressure to keep leaks in check Keeping leaks in check is a major challenge for water companies but one that can be met with variable speed drives to... Read More >
- Going green at Severn Trent's Minworth STW With a £60 million investment aimed at producing 30 per cent more green energy from its largest sewage treatment works,... Read More >
- Case Study: Pumping up quality at Burnham Jetty A year's worth of planning, seamless collaboration and technical expertise were crucial to the success of a complex... Read More >
- Thames Water rolls out energy-reducing sludge pump solution A smart air injection (SAI) system combined with progressive cavity pumps is proving key to more efficient sludge handling... Read More >
- Overcoming the issues of transporting dewatered sludge With Ofwat seeking to promote sludge trading to secure best value, efficient transportation solutions are required, SEEPEX... Read More >
- Case study: A customised pump solution for Hinkley Point A bespoke pumping system is proving key to the water management strategy for the major nuclear project in Somerset Read More >