Hidrostal solves problematic pump issue in residential development
When a network pumping station in the Anglian Water region was suffering from repeated blockages, a more effective replacement was found with the help of Hidrostal
Hidrostal, specialist pump manufacturers for the wastewater industry, were approached by Anglian Water when a network pumping station situated in the village of Harleston, Suffolk was proving problematic.
The wet well raw sewage pumping station is gravity fed from the surrounding residential development which accepts the common waste from domestic properties and can vary in its content owing to the accumulation of wipes, fats, oils and greases. This contributes to the potential for rag build up making the pumps more susceptible to blockages.
An increase in reactive maintenance costs, disproportionate with its size and capacity, coupled with an increase in residential complaints, meant the site was becoming untenable. The annual reactive maintenance costs were amounting to a value exceeding 300% of the original purchase cost of just one pump unit. Reactive maintenance covers unscheduled or unplanned visits to any asset outside of its scheduled maintenance programme. These visits can often entail out of hours emergency call outs, unscheduled tankering, increased wet well cleaning cycles and lifting and de-ragging of pumps.
The original pumps on this site were installed for their energy benefit and innovative designs but had not been able to cope with the waste water from this development. One of the units was replaced in favour of the Hidrostal Screw centrifugal impeller pump. Hidrostal’s single screw centrifugal impeller design was chosen because of its increased free passage and rag handling capabilities whilst retaining a high level of hydraulic efficiency. The replacement pump was retrofitted with minimal disruption to the existing installation which was on a permanently installed guide rail mounted system.
Since the installation of the Hidrostal pump 18 months ago, there has been zero reactive call outs and the station is back to a single scheduled annual wet well clean and maintenance visit. The local technician even joked that there would be a greater need for garden maintenance than pumping station maintenance.
“Hidrostal are delighted to have solved the pumping problems for both Anglian Water and the local residents of Harleston village,” concluded the company. “With solids handling capabilities that are second to none, Hidrostal’s pumps once again proved to be the best choice for pumping high rag laden sewage.”
- Comment: Ease off the pressure to keep leaks in check Keeping leaks in check is a major challenge for water companies but one that can be met with variable speed drives to... Read More >
- Pump maintenance: keeping it pumping Maintaining pumps in top condition is a vital consideration in the totex equation for pumping assets, and water utilities... Read More >
- Ready for anything: Resilience in the Round Resilience is one of the four priorities that Ofwat wants to see water companies adopt in their plans for PR19. But what... Read More >
- Flood resilience: what you need to know Geoff Williams, northern sales manager at Sykes Pumps, discusses the need for businesses and local authorities to think... Read More >
- Reaching net carbon zero In summer 2019, the water industry committed to reach net carbon zero by 2030. This is a very ambitious aim and... Read More >
- Rewarding excellence WWT content director Alec Peachey looks ahead to next year's Water Industry Awards. Read More >
- Going green at Severn Trent's Minworth STW With a £60 million investment aimed at producing 30 per cent more green energy from its largest sewage treatment works,... Read More >
- Case Study: Pumping up quality at Burnham Jetty A year's worth of planning, seamless collaboration and technical expertise were crucial to the success of a complex... Read More >