Reducing harmonics with passive filters or active front-end drives
Harmonics in the electrical systems of operators can be addressed by front-end drives or passive filters, with each having their advantages and drawbacks
Harmonics are caused by non-linear loads on the network, such as fluorescent lights, computers and AC drives. When adding further drives at a site, the total harmonic load must be considered.
Most drives have six-pulse diode rectifiers, which give relatively high levels of total harmonic distortion, about 40 percent. Twelve-pulse rectifiers were introduced some years ago, which reduce total harmonic distortion to about 12 percent. However, in recent years, their place has been taken by active front-end drives. These have a total harmonic distortion of only two to four percent.
With an active front-end drive, harmonics are dealt with inside the drive and never enter the network. This contrasts against the traditional solution, which is to filter out harmonics after they have been created. The active front-end drive is a safe and easy option, guaranteed not to add damaging harmonics to the network. Unlike passive filters, it also coexists happily with generators on the network.
An alternative solution is to use a six-pulse diode rectifier plus a passive filter, sometimes with significant drawbacks as a result. A fairly high level of harmonics may still exist on the network, even after a passive filter has been installed.
Problems may occur in networks that have an imbalance between the phases, as the case is in many rural networks. Under these conditions, the passive filter is less effective. The problems can be especially severe at low load, around 20 percent. Here, distortion may increase from, say, 8 to 12 percent.
Comparisons between passive filters and low harmonic drives are frequently made at full load. However, a true comparison should be made around 75 percent load, which is closer to the actual operating point for most pump motors at reduced load.
The increase in losses tends to be greatest in low power installations. For instance, a 22 kW six-pulse drive with a 43 A filter can have losses of 873 W, while a low harmonic drive of the same size has losses of 490 W, which means the losses of the filter solution are a full 78 percent higher.
Some passive filters are only effective at the lower end of the harmonic spectrum. Also, power factor can be very poor at low load: 0.5 at 20 percent would not be unusual.
The active front-end drive is easier to install, as you only have to consider the mains voltage, the pump absorbed power and the fault level of the network. The filter also needs to be disconnected at low load, which means that there needs to be a discussion with the panel builder about additional circuitry to achieve this and how this should be designed.
A passive filter can weigh as much as 225kg, which might make it difficult to lift and fit in the panel. Additionally, each filter must be designed according to the needs of the site at a specific time. If conditions change, the filter may have to be changed.
Passive filters should only be considered when there is a small network with a small number of pumps, no generator supply and consistent load conditions. Under these circumstances, the passive filter can provide a cost benefit. Otherwise, it is safest to go with a low harmonic drive.
To find out more about tackling harmonics, including how to register for ABB’s free Lunch ‘n’ Learn training session, visit: http://new.abb.com/uk/campaigns/water-totex/water-harmonics
- Anglian Water to carry out solar installation Anglian Water is set to carry out an installation of solar panels at one of its key operational sites in Huntingdonshire... Read More >
- GB ranked second for water and sewerage services A new international survey has revealed that the satisfaction rating for Great Britain's water and sewerage services is... Read More >
- Wet wipe ruling welcomed by water companies Water companies have welcomed a ruling saying wet wipe manufacturers need to be clearer when they are marketing their... Read More >
- Why asset management matters 01/11/2017 09:40:03 Keeping a detailed asset inventory at a treatment works is a must, and is the first step towards an effective asset...
- The new approach to energy efficiency 26/07/2017 09:32:21 Many pump systems are far less energy efficient than they appear to be, and optimising electrical systems is the key
- The Big Picture on Energy Costs 26/05/2017 11:58:26 Details matter when it comes to pump system energy assessments, which is why not all assessments are the same