South West Water has to pay £205K for Fal sewage spill
South West Water (SWW) has been ordered to pay £205,000 in fines and costs for sewage spill that forced mussel and oyster beds to close in the Fal estuary in Cornwall.
On August 26, 2013, untreated sewage overflowed from the water company’s Newham sewage treatment works near Truro into the Fal, an internationally important shellfishery, Site of Special Scientific Interest (SSSI) and Special Area of Conservation (SAC).
The illegal spill occurred after a piece of redundant grating fell and partially blocked an inlet at the works, causing sewage to back up and overflow into the estuary via a storm storage outfall. The spill continued for about 9.5 hours, during which time enough sewage escaped to fill 4,563 bath tubs (730,000 litres).
The discharge occurred close to mussel and oyster beds at Malpas and Grimes Bar. As a precaution, these shellfisheries were temporarily closed by Cornwall Port Health Authority because of the possible risk of contamination by harmful viruses and bacteria such as Norovirus and e.coli.
The decision to close the shellfish beds was taken just before the start of the commercial harvesting season (October 1). Although most harvesting is done during the commercial season, there is a risk small quantities of shellfish may be hand-picked by individuals outside of this time and there would have been a potential risk to those consumers.
Sewage at the Newham treatment works normally undergoes a high level of treatment (tertiary) including ultraviolet (UV) that kills bacteria and disinfects effluent. The UV disinfection system is required at this site because of the Fal estuary’s designation as a shellfishery.
The sewage discharged over a bank holiday on August 26 was settled and screened, but otherwise untreated and occurred outside of a storm event. This would have resulted in a significant increase in levels of bacteria in parts of the Fal estuary and meant the treatment works was in breach of its Environment Agency permit.
Mark Pilcher, team leader for the Environment Agency in west Cornwall, said: “It is essential large sewage works bordering estuaries with conservation designations and also containing shellfish beds are operated and inspected to a high standard to prevent unpermitted sewage spills posing risks to public health and the environment. In this case an inspection programme or removal of a redundant grating structure would have removed the risk of this grating falling into the sewage works and blocking it leading to the spill of sewage.”
SWW was fined £185,000 plus £20,000 costs after pleading guilty to two offences under the Environmental Permitting Regulations 2010 including, on August 26, 2013, causing pollution of the Fal estuary through the illegal discharge of sewage and failing to maintain a saline tank valve at its Newham sewage treatment works. The company was fined £175,000 for the first offence and £10,000 for the second.
The case, brought by the Environment Agency, was heard at Truro Crown Court on February 15, 2017.
- Laundry firm fined for fire hydrant water abstraction Tamar Laundry has been fined £750 by Bodmin Magistrates Court for illegally abstracting water from a fire hydrant. In a... Read More >
- Thames Water fined over street works notification failure Failing to correctly notify street works has led to Thames Water Utilities (TWU) being fined by Newbury Magistrates Court.... Read More >
- Aqualogy wins Thames energy from sludge contract Bristol-based firm Aqualogy Environment Ltd has been awarded a contract for advanced energy recovery from sludge by Thames... Read More >
- Project Focus: Affinity Water in metaldehyde detection trial A trial at an Affinity Water treatment works in Hertfordshire has demonstrated the effectiveness of modifying lab... Read More >
- Research Notes: The wastewater headache after taking an aspirin Trace contaminants, including chemicals from pharmaceutical and household products that are part of our daily lives, are a... Read More >
- Innovation Zone: Metaldehyde - a Pest of a Problem Amongst the agricultural pesticides that find their way into raw water sources, metaldehyde - which is used in slug... Read More >
- Interview: John Devall, Water Director, Northumbrian Water "Customer perception should be your reality - it's the ultimate barometer." Read More >
- Digging Deeper: Blocking leaden dangers With the dangers of lead in water highlighted recently by the case of the US city of Flint in Michigan, pipe expert Nick... Read More >
- Supply Network Manager Starting salary: Grade SF £30,767 - £41,226 Job description: Looking for your next career move in water supply? If so, we may have a fantastic... Read more here.
- Repair and maintenance ganger (team leader) Taunton Location: Taunton Starting salary: Dependent on experience and training certificates, plus standby allowance and call out Package: 45... Read more here.
- Repair and maintenance ganger (team leader) Yeovil Location: Yeovil Starting salary: 26,520 - 28,560 salary dependent on experience and training certificates, plus standby allowance and call... Read more here.
- Repair and maintenance ganger (team leader) Cossington Location: Cossington Starting salary: £26,520 - £28,560 salary dependent on experience and training certificates, plus standby allowance... Read more here.