Scottish Water fined for sewage pollution at Doune
Stirling Sheriff Court has fined Scottish Water £6,000 for causing untreated sewage to enter the Dragon Burn, a tributary of the River Teith. The utility pleaded guilty to allowing untreated sewage to enter a combined sewer and emergency overflow that subsequently discharged to the Dragon Burn between March 11 to 15, 2012.
The incident was investigated by the Scottish Environment Protection Agency (SEPA) after it received a complaint from a member of the public regarding pollution of the Dragon Burn in Doune.
A SEPA officer inspected the Dragon Burn at George Street about 100m upstream of the Scottish Water sewage pumping station at Doune Fire Station, the watercourse was running clear. However, about 275m downstream, a significant deposition of sewage related debris and sewage fungus could be seen on the banks and bed. There was also a significant growth of sewage fungus in the burn and the water was running grey in colour. Sewage deposits were running the full 275m.
An inspection at the surface outfall of the sewage pumping station showed there was a discharge of what appeared to be sewage to the Dragon Burn from the surface outfall pipe. This is the outfall used as the combined sewer overflow and the emergency overflow.
Officers checking the telemetry control panel at the sewage pumping station found that Pump 1 had tripped or overloaded and Pump 2, the Duty Pump, was stopped. Subsequent correspondence with Scottish Water revealed that the discharge occurred when both pumps at the station failed and the wet well then filled resulting in a spill to the watercourse. There was also a fault within the Remote Telemetry Unit and no alarms were recorded over the past three months.
Calum Waddell, SEPA’s investigating officer, said: “The failure of both pumps within Doune Fire Station sewage pumping station meant no sewage was being passed forward for treatment resulting in the discharge of sewage to the Dragon Burn. This could have been avoided if the station had operational alarms in place to alert staff to any problems with the pump.
"In addition, the operators of the station were unaware of the presence of the screens, and so they were not maintained and couldn’t do their job when needed. This caused the significant debris in the watercourse, exacerbating the entire pollution incident."
- Anglian fined £50k for Essex sewage spill Anglian Water has been fined £50,000 after sewage contaminated a brook through an emergency overflow pipe killing more than... Read More >
- Sewage treatment works shutdown strategy saves time and money A way to shutdown an entire sewage treatment works without using storm facilities has been devised by a Costain team... Read More >
- Thames Water ordered to pay more compensation to sewer flooding victims Thames Water has lost an appeal to pay a smaller fine and less compensation to victims of sewer flooding. Instead, the... Read More >
- Anglian Water ends long search to improve pump station efficiency After nearly six years, Anglian Water has finally found a solution to improve efficiency at one of the largest raw water... Read More >
- Hidrostal solves problematic pump issue in residential development When a network pumping station in the Anglian Water region was suffering from repeated blockages, a more effective... Read More >
- What will the pump of the future look like? How will the pump play its part in the digital future represented by industry 4.0? Bryan Orchard explores how one... Read More >
- Component pricing: a disposable dilemma When working out the whole-life cost of a pump or similar equipment, one variable is how often components need to be... Read More >
- Interview: Duncan Lewis, Managing Director, Xylem Whether it is data capture, servicing and maintenance or energy-saving optimisation, pump manufacturers now offer so much... Read More >