Scottish Water fined for sewage pollution at Doune
Stirling Sheriff Court has fined Scottish Water £6,000 for causing untreated sewage to enter the Dragon Burn, a tributary of the River Teith. The utility pleaded guilty to allowing untreated sewage to enter a combined sewer and emergency overflow that subsequently discharged to the Dragon Burn between March 11 to 15, 2012.
The incident was investigated by the Scottish Environment Protection Agency (SEPA) after it received a complaint from a member of the public regarding pollution of the Dragon Burn in Doune.
A SEPA officer inspected the Dragon Burn at George Street about 100m upstream of the Scottish Water sewage pumping station at Doune Fire Station, the watercourse was running clear. However, about 275m downstream, a significant deposition of sewage related debris and sewage fungus could be seen on the banks and bed. There was also a significant growth of sewage fungus in the burn and the water was running grey in colour. Sewage deposits were running the full 275m.
An inspection at the surface outfall of the sewage pumping station showed there was a discharge of what appeared to be sewage to the Dragon Burn from the surface outfall pipe. This is the outfall used as the combined sewer overflow and the emergency overflow.
Officers checking the telemetry control panel at the sewage pumping station found that Pump 1 had tripped or overloaded and Pump 2, the Duty Pump, was stopped. Subsequent correspondence with Scottish Water revealed that the discharge occurred when both pumps at the station failed and the wet well then filled resulting in a spill to the watercourse. There was also a fault within the Remote Telemetry Unit and no alarms were recorded over the past three months.
Calum Waddell, SEPA’s investigating officer, said: “The failure of both pumps within Doune Fire Station sewage pumping station meant no sewage was being passed forward for treatment resulting in the discharge of sewage to the Dragon Burn. This could have been avoided if the station had operational alarms in place to alert staff to any problems with the pump.
"In addition, the operators of the station were unaware of the presence of the screens, and so they were not maintained and couldn’t do their job when needed. This caused the significant debris in the watercourse, exacerbating the entire pollution incident."
- Wessex Water's civil sanction for polluting River Trym An Enforcement Undertaking (EU) from Wessex Water Services has been accepted by the Environment Agency (EA). It is the... Read More >
- London needs integrated water management strategy, says report Drinking water shortfalls and contaminated flooding caused by sewage overflow are among the risks facing London unless a... Read More >
- UK's first heat-from-sewage scheme opens in Scotland Scottish Water has today (8 December) overseen the launch of the UK's first heat- from-sewage scheme at Borders College... Read More >
- Powering the pumps: electric or diesel? The question of which power source to use for portable pump sets can be a difficult one, with both electric and diesel... Read More >
- Archimedes screw pumps boost infrastructure in Mansfield Archimedes screw pumps may work on a centuries-old design but they are still the most efficient way of lifting water over... Read More >
- Comment: Brexit and the pump industry Exiting the European Community and dismantling our ties to EU Laws, via the Government's introduction of the Great Repeal... Read More >
- Round Table: Pumps and energy Performance monitoring supported by technology and condition-based maintenance are two of the key factors in optimising... Read More >
- Getting to Grips with… dosing pumps Dosing pumps are mission critical appliances that must operate reliably and efficiently, as the success of processes such... Read More >
- Head of Tendering & Design Salary Range: Commensurate with roleThe Tendering & Design Department plays a critical role in turning customer enquiries in to fully costed... Read more here.
- Head of Operations Salary Range: Commensurate with role Head of Operations: The Head of Operations will be responsible for the successful day to day delivery... Read more here.
- Waste Water Network Manager c. £42,000 depending on skills and experience An exciting opportunity has arisen for the role of Wastewater Network Manager within the Asset... Read more here.
- Deputy Directors – multiple roles The Office of Rail and Road (ORR) is the independent economic and safety regulator for Britain’s railways, overseeing an industry that carried... Read more here.