Pump failure earns NI Water £1,000 fine
NI Water was convicted yesterday (August 1) at Belfast Magistrates' Court of causing a water pollution incident at Mallusk, County Antrim in 2015.
The company Tpleaded guilty and was fined £1,000 plus £15 Offenders Levy for breaching the conditions of a discharge consent relating to the operation of Hydepark No.2 Wastewater Pumping Station (WwPS) located on Blackwater Road, Mallusk, County Antrim.
On August 24, 2015, a Water Quality Inspector (WQI) acting on behalf of the Northern Ireland Environment Agency (NIEA) responded to a report of pollution in the Mallusk area affecting the Ballymartin Water, Mallusk. The next day, inspectors returned to Mallusk Park Industrial Estate to continue the investigation.
In a statement made under caution, NI Water stated that ‘a discharge occurred as a result of a failure of the second of two pumps at Hydepark No.2 WwPS on 23 August 2015’.
NIEA’s investigation determined that a second standby pump, the provision of which is a condition of the Department’s Consent to Discharge, had not been available at the pumping station for a number of weeks prior to the incident. If available, the second standby pump would have come into operation following the failure of the duty pump thereby preventing discharge from the station.
This situation contravened the conditions of a Water (NI) Order 1999 Consent to Discharge issued by the Department in respect of the installation.
- Welsh Water tenders for four Dwr partners Dwr Cymru Welsh Water (DCWW) is seeking up to four Delivery Alliance Partners to deliver its AMP6 capital delivery... Read More >
- Councillors get the low-down on odour at Blackburn Meadows Councillors from Rotherham Metropolitan Borough Council having been discovering how Yorkshire Water is working to reduce... Read More >
- Cable management system provides solution for Severn Trent grit A new cable management system has proved the key to the more effective dredging of grit at a sewage treatment works... Read More >
- Offsite build for Affinity pumping station Taking a pioneering new approach to a borehole pumping station upgrade in Essex, Affinity Water minimised asset downtime... Read More >
- Anglian Water ends long search to improve pump station efficiency After nearly six years, Anglian Water has finally found a solution to improve efficiency at one of the largest raw water... Read More >
- Hidrostal solves problematic pump issue in residential development When a network pumping station in the Anglian Water region was suffering from repeated blockages, a more effective... Read More >
- What will the pump of the future look like? How will the pump play its part in the digital future represented by industry 4.0? Bryan Orchard explores how one... Read More >
- Component pricing: a disposable dilemma When working out the whole-life cost of a pump or similar equipment, one variable is how often components need to be... Read More >