Emergency drive hire avoids pollution risk for Anglian
The loan of a variable speed drive (VSD) at short notice ensured that Anglian Water avoided the risk of a sewage leak at one of its pumping stations in Essex.
The utility hired a VSD from Gibbons Engineering Group, an ABB-authorised value provider, to ensure that the Great Stambridge pumping station was back in operation within a day.
The pumping station, near Rochford in Essex, features three dry well submersible pumps, pumping sewage to the wastewater treatment works. Two ABB drives are used for two of the pumps. The remaining pump operates on-line as an emergency standby. In a 24/7 operation, the VSDs operate the pump motors as the wastewater level rises, modulating the speed of the pumps to account for the level changes.
Depending on the level, a maximum flow is achieved from two of the pumps operating simultaneously. The two VSDs ensure the system pumps at a pre-set maximum flow rate of 300 litres per second, equivalent to a motor speed of 46 Hz. This flow rate is the maximum the treatment works can handle without overwhelming the screens used to trap rags, large solids and other debris.
Brad Colledge, Anglian Water’s maintenance engineer responsible for the site, said: “An engineer reported that he could not access the drive’s key pad to change its settings. For some reason the drive would not store the motor data in its memory.
“With the loss of one pump, our pumping capacity was seriously reduced. If we had lost another pump, we would have faced the risk of the incoming flow exceeding the outgoing flow, leading to a serious danger of a sewage overflow from the site that could contaminate local water courses.”
Gibbons supplied a 110 kW drive as part of its hire scheme, which installs drives on a temporary basis to cover emergencies such as this or as part of a trial to prove the effectiveness of VSDs in saving energy.
The hire drive was in operation the next day and operated for three weeks while the regular drive was being repaired by Gibbons.
- Pump failure earns NI Water £1,000 fine NI Water was convicted yesterday (August 1) at Belfast Magistrates' Court of causing a water pollution incident at... Read More >
- Northumbrian upgrades Hartlepool sewage pumping station Northumbrian Water is modernising one of its sewerage assets in the Hartlepool area. The £250,000 scheme will increase the... Read More >
- EMCOR UK wins Anglian facilities contract EMCOR UK has been awarded a contract by Anglian Water to perform integrated facilities management services across 84 of... Read More >
- Archimedes screw pumps boost infrastructure in Mansfield Archimedes screw pumps may work on a centuries-old design but they are still the most efficient way of lifting water over... Read More >
- Comment: Brexit and the pump industry Exiting the European Community and dismantling our ties to EU Laws, via the Government's introduction of the Great Repeal... Read More >
- Round Table: Pumps and energy Performance monitoring supported by technology and condition-based maintenance are two of the key factors in optimising... Read More >
- Getting to Grips with… dosing pumps Dosing pumps are mission critical appliances that must operate reliably and efficiently, as the success of processes such... Read More >
- Ending the nightmare of wet-wipe pump blockages An ingenious device developed in partnership with Scottish Water promises to reduce wastewater pump maintenance by... Read More >