Works trials split bearings
Maintenance time and cost has been reduced by a new approach to bearings in a Wessex Water treatment plant, says Adrian Menzies of Revolvo
An initial trial of four split roller bearings (SRB) units has been undertaken at a Wessex Water wastewater treatment works. Wessex Water operates wastewater and water networks throughout South-west England.
Several of the company’s wastewater sites incorporate orbital aeration tanks as part of the sewage treatment process. Each of these tanks has a number of horizontal rotors which agitate the sewage and introduce oxygen, thereby accelerating the treatment process.
In the past, the rotors have always been supported by two solid bearings with internal seals. However, this arrangement has not proved ideal. During periods of heavy rain it is possible for the sludge level in the aerator tanks to rise to the point where the bearing units become temporarily submerged, compromising the bearing seals and leading to premature bearing failure.
Replacement presents its own set of problems. In order to change out the solid bearings, each rotor must be lifted clear of the tank. Furthermore, depending on the level of corrosion, the rotor may then have to be completely removed for workshop based remedial work. In either case, the most substantial part of the cost is crane hire, which can be in excess of £2,500 per day.
Revolvo undertook a full evaluation of the existing application conditions and proposed a solution based upon its SRB range. The split bearing units were specified with housings and supports designed to be interchangeable with the existing bearing units wherever possible, or incorporate adaptor plates if necessary.
The trial period was undertaken throughout the winter months and contained several periods of heavy rainfall, subjecting the SRB to a number of high water level situations. Despite this, the bearings performed to expectations and continue to run smoothly and reliably.
The split-to-the-shaft design and advanced sealing of Revolvo’s SRB allow easy maintenance without having to remove the shafts of long horizontal rotors that agitate sewage and introduce oxygen to the treatment process. In addition, the sealed SRBs are designed to withstand full submersion in sewage sludge, which can occur due to raised levels in the aerator tanks during periods of heavy rainfall.
The housings were also equipped with high performance split rubber lip seals with garter springs and retaining plates, to guard against water ingress during intermittent submersion. Finally, and importantly, the bearings were equipped with remote grease points that allow maintenance without engineers ever having to come into contact with the sludge.
The use of SRB bearings promises large future cost savings for Wessex Water. Should the need arise in future to change a SRB split bearing, it will only be necessary to support the rotor shaft, eliminating the necessity and cost of crane hire. This in itself will easily recover the investment of using the SRB split bearing units.
- Water companies track down private pumping stations Water and sewerage companies in England and Wales face a deadline of 1st October 2016 for adopting most private pumping... Read More >
- Flood management: making more of less As the cuts to flood management budgets bite, David Keiller, technical director, Black & Veatch Europe, Middle East,... Read More >
- Drinking water reed bed system nears completion The many benefits of natural wastewater systems will be illustrated by a £4.5M system scheduled to be up and running in... Read More >
- Eco-friendly phosphorus removal: Soneco boom Amid the clamour for effective new means of phosphorus removal, Power & Water CEO Gareth Morgan discusses his... Read More >
- Opinion: Add trees for a future water-friendly landscape The time is now to put trees at the heart of land management policy and reap all the benefits they provide, The Woodland... Read More >
- Water companies and BIM: realising the potential The utilities sector has lagged behind in implementing BIM, and has yet to fully realise its potential for maintenance as... Read More >
- Innovative survey technology helps CWA pipeline project A £10M project that saw CWA add a duplication main in North Lanarkshire involved the use of PureTech's PipeDiver... Read More >
- Opinion: Collaborating will be crucial after PR19 A collaborative approach to innovation must sit at the heart of PR19 strategies, writes Tim Edwards Read More >