Overpumping solution helps Anglian sludge management
When routine maintenance was required on business-critical sludge assets at Anglian Water's Caister WRC, a temporary pumping solution provided the answer
by Rob Richards, Sykes Pumps
A business critical temporary pump solution was required at Anglian Water’s Water Recycling Centre in Caister, Norfolk, in order to manage return activated sludge levels during infrastructure maintenance. The wastewater treatment processes at Anglian Water’s Caister Water Recycling Centre rely on careful management of the return activated sludge (RAS) in the final settlement tanks.
Rich in enzymes that help to clean the water and remove unwanted bacteria, the RAS is critical to both the first and final elements in the wastewater treatment process.
A sludge blanket needs to be managed at the correct levels in the final settlement tanks to maintain and improve the water quality before it is released into the watercourses. The RAS content required in the final settlement tanks varies depending on the throughput of wastewater at the facility.
Meanwhile, the RAS that is not required in the final settlement tanks is returned to the primary processing tanks at the head of works as an essential component in beginning the processing cycle.
Too much RAS in the final settlement tanks, or too little in the initial processing, could have a critical impact across the whole water recycling centre. When routine maintenance was required to the adjustable bellmouths used to control the amount of RAS taken from the final settlement tanks and returned to the head of works, Anglian Water needed a temporary overpumping solution that would enable the bellmouths to be taken off line, while ensuring that the correct levels of sludge were returned to the head of works and maintained in the final settlement tanks.
As a category A supplier to Anglian Water, IOS (Integrated Operational Solutions) developed a suitable solution and, following a site visit to fully assess the requirements, six duty pumps were specified for the overpumping requirements, with an additional three pumps provided to site as standby units.
Sykes Pumps deployed six Super Wispaset 200 8” diesel pumps, each with a flow rate of up to 580m3 per hour, with one each at final settlement tanks 1,2,3 and 4. An additional two Super Wispaset 200 pumps were installed for standby use. For tanks 5 and 6 where the required flow rate was lower, a 6” Super Wispaset 150 pump was specified for each tank, with a further 6” pump installed as standby.
The pumps were supplied to site with four fuel tanks, 174m of 8” wire armour hose, 84m of 6” wire hose, 84m of 8” polyurethane piping and 42m of 6” polyurethane piping. This enabled Anglian Water IOS to connect the pumps to the existing pipework so that sludge could be pumped directly into the network for transferring RAS from the final settlement tanks back to the head of works, while bypassing the chambers where the bellmouths are located during the repair works.
The fuel tanks ensured that the pumps could run constantly over the course of the overpumping operation without risk of interruption, while daily site visits from Sykes Pumps technical team ensured that the pumps were checked and in excellent working order at all times.
Managing the flow
As the bellmouths are usually used to control the flow of the RAS from the final settlement tanks, management of the flow rates had to be built into the overpumping installation. Anglian Water’s engineers fitted control valves into the pipe gallery below ground and these were manually connected to a temporary piping manifold and operated via an iOS control system.
Anglian Water’s IOS site team was then able to adjust the flow by monitoring sludge blanket levels using telemetry technology installed on all the pumps as part of the pump hire specification. This allowed 24/7 remote monitoring of flow rates so that these could be adjusted in real time if the sludge blanket needed to be increased or reduced.
Although the pumps were on hire for two weeks, the overpumping operation itself was required for just three days while the RAS lanes were out of commission.
The overpumping was so process critical, however, that significant due diligence was involved in the specification and installation stages, with a week invested in installing, commissioning and testing the overpumping capability before management of the RAS was transferred to the temporary set up.
Decommissioning was a similarly meticulous process, carried out over the course of a week following the reinstatement of the bellmouths.
The project was successfully completed in February with zero risk of process interruption throughout.
- Southern spends £25M to meet NEP conditions Due to the need to cut nitrogen levels in effluent being discharged into the River Test, Southern Water has invested £25M... Read More >
- Peristaltic pumps prove the right dose for Welsh Water Switching from diaphragm to peristaltic pumps for chemical dosing helped Dwr Cymru Welsh Water save Opex costs while... Read More >
- PMP gets Yorkshire Water out of a tight spot A complicated wet well posed a health and safety risk that was overcome with some adaptations and an emergency rescue dummy... Read More >
- Archimedes screw pumps boost infrastructure in Mansfield Archimedes screw pumps may work on a centuries-old design but they are still the most efficient way of lifting water over... Read More >
- Comment: Brexit and the pump industry Exiting the European Community and dismantling our ties to EU Laws, via the Government's introduction of the Great Repeal... Read More >
- Round Table: Pumps and energy Performance monitoring supported by technology and condition-based maintenance are two of the key factors in optimising... Read More >
- Getting to Grips with… dosing pumps Dosing pumps are mission critical appliances that must operate reliably and efficiently, as the success of processes such... Read More >
- Ending the nightmare of wet-wipe pump blockages An ingenious device developed in partnership with Scottish Water promises to reduce wastewater pump maintenance by... Read More >
- Supply Network Manager Location: Somerset Salary: £30,767 to £41,226 per annum Looking for your next career move in water supply? If so, we may have a fantastic... Read more here.
- Senior Analyst The Organisation The Water Industry Commission for Scotland is the economic regulator of the water and sewerage industry in Scotland. ... Read more here.
- Key Account Manager Key Account Manager Competitive Salary: £40,000+ DOE London and Thames Valley Knowledge, Skills & Experience Commercially astute with... Read more here.
- Contracts Manager Contracts Manager Castle Water Limited Castle Water is the leading independent water retailer in the UK, and one of the fastest growing... Read more here.
- Divisional Customer Services Director Castle Water is the leading independent water retailer in the UK, and one of the fastest growing utility supply companies, supplying services... Read more here.