Getting to Grips with... sewer jetting
Jetting is an important tool for clearing sewer blockages, but care must be taken to use the right pressure for the pipe materials, writes Stuart Crisp
by Stuart Crisp, Business Development Director, Concrete Pipeline Systems Association (CPSA)
A sewer blockage is bad news. It can prevent or reduce the flow of wastewater through the pipe causing its contents to back up underground until it eventually overflows from manholes in roads and gardens and even from toilets. Data suggests that sewer blockages result in around 4000 property flooding incidents each year in England and Wales. In the UK, blocked sewers are often cleared using high pressure water jetting; as such, it is generally considered an emergency operation.
Q: What is sewer jetting?
A: High pressure jetting is one of the main methods used to clean drains and sewers and to clear blockages. Jetting involves water being forced along a hose and through a nozzle at high pressure. Various nozzle/water jet configurations are available, with selection depending on pipe diameter and whether the nozzle is being used to release a blockage or for general cleaning.
Q: Is there a limit on the jetting pressure that can be used to clear a blockage?
A: The standard BS EN 14654-1:2014 Management and control of operational activities in drain and sewer systems outside buildings, Part 1: Cleaning states that when jetting: “Maximum working pressures to avoid damage will vary according to the material of the pipe, condition of the pipe and type of nozzle”.
In 2005, the Water Research Council (WRc) published the Second Edition of the Sewer Jetting Code of Practice. This document provides guidance on good working when using high pressure jetting equipment. The code sets out the maximum jetting pressure for pipeline materials, varying from 1500psi for brick sewers, 2600psi for plastic, up to 5000psi for concrete and clay pipelines.
In theory, best practice guidance should ensure damage to the fabric of drains and sewers is avoided but, with a variation of 3500psi between the maximum jetting pressure for brick and concrete and the need to identify the pipe material prior to clearance operations commencing, there is the potential for abuse.
Q: Why are some pipes more at risk of jetting damage than others?
A: High pressure water jetting resilience is a function of the hardness of the pipe material and the thickness of the pipe wall. The reason plastic pipes are considered to be more vulnerable to jetting damage than concrete or clay, for example, is not directly attributable to the hardness of the pipe material but to the thickness of the pipe wall. Plastic pipes generally have very thin walls and any loss of material arising from jetting can result in a significant reduction in overall wall thickness or even penetration through the pipe wall. In contrast, rigid pipes such as concrete have thick walls so that any loss of material that may arise from high pressure water jetting is, generally, inconsequential to the overall performance of the pipe.
Q: Should jetting pressure be standardised?
A: Most reputable jetting contractors will be aware of the need to identify the material from which the sewer is manufactured and limit the jetting pressure accordingly. If, however, a blockage fails to clear or if a jetting contractor has not established the material from which a pipe is manufactured, it is not unknown or, indeed, unexpected for a contractor under such circumstances to clear an obstruction by increasing the pressure until the obstruction shifts which, depending on the pipe material, could potentially damage the pipe and joints.
Plastic pipe manufacturers argue that because their pipes are generally smoother, then a lower jetting pressure can be used to either clean the pipeline or remove a blockage to reinstate hydraulic performance. Nevertheless, the risk remains that a jetting contractor could use a higher pressure to clear a stubborn blockage, which could lead to a greater risk of damage of thin-walled plastic pipes in particular.
It is generally accepted that smaller diameter pipes are most effectively cleaned using high pressure water as the source of energy within the pipe. In fact, in the past some water companies have specified a jetting resilience of 4000psi for sewers. It would help eliminate confusion if this pressure limit was to be applied consistently for all smaller sewers by all water companies.
Q: How has the transfer of domestic foul sewers and lateral drains to water companies in England and Wales impacted material selection?
A: Water utilities have been keen to ensure that pipelines do not become damaged by pressure jetting or other mechanisms and that adopted drains and sewer assets transferred from new private developments attain a minimum level of performance.
Thames Water, for example, in its addendum to Sewers for Adoption 7th Edition, calls for additional testing of plastic pipelines and the selection of non-polymeric components where air testing would be hard to achieve.
“Thames Water requires any plastic pipes to be subjected to an air test as part of the final inspection to verify that they have not been damaged while under the developer’s control, irrespective of any earlier testing that may have been done. Developers shall carry out the air testing during the final inspection with TWUL as witness. Developers are recommended to consider the selection of non-polymeric components in locations where air testing requirements will be hard to achieve during final inspection, or in areas where the rectification of jetting damage will be costly to assess and repair. Adoptions Engineers may stipulate the use of rigid materials where no suitable method of air-testing is available for review during the adoptions application”.
Anglian Water has a similar requirement for taking ownership of domestic lateral drains. Its guidance document states that: “The use of plastic pipes will not be permitted unless the pipe can withstand 4000psi jetting pressure”.
It’s a convincing argument for the use of rigid pipe materials such as concrete.
Q: Are there any alternatives to high pressure jetting?
A: For larger diameter pipelines there is an argument that flushing the blockage through using a large volume of water at lower pressure, through the use of larger bore nozzles, is an alternative to high pressure jetting. This option does have the advantage that the higher volume of water should carry sufficient energy to flush debris to a manhole for removal, while posing a lower risk of damage to the pipe.
To generate a high water flow rate, a jetting contractor will often need access to a drinking water hydrant or, where no hydrant is available, large capacity water tankers may be required to supply the necessary volume of cleansing water. This is obviously a more expensive, wasteful, less environmentally friendly option than using a lower volume of water jetted at a higher pressure. But, if a sewer pipe is fabricated from a material that is vulnerable to damage from high jetting pressures, such as plastic, then lower-pressure high-flow flushing may be the only option available to those charged with clearing the blockage.
-For more information on sewer jetting go to www.concretepipes.co.uk
- Ductile offers advantages Polyethylene pipes are continuing to replace older metal-based networks, despite reports of them leading to high levels of... Read More >
- Getting to Grips With... Section 104 agreements Drains and sewers are a vital part of any new housing development, and developers need to make early decisions on their... Read More >
- Innovation Zone: SewerBatt This month, we look at technology which uses acoustic signals to allow the rapid inspection of sewers and drains for... Read More >
- Getting to Grips with... sewer jetting Jetting is an important tool for clearing sewer blockages, but care must be taken to use the right pressure for the pipe... Read More >
- Fats, oil and grease need clear thinking Latest research from Cranfield has shone a light on the characteristics of of fats, oil and grease (FOG) droplets entering... Read More >
- Getting to Grips with... Ice Pigging An innovative method of cleaning pipes, ice pigging is now being seen as a viable option for wastewater as well as clean... Read More >
- Interview: Professor Dragan Savic, Exeter University "If you can't measure, you can't manage - and the most uncertain element of water management is the demand." Read More >
- Interview: Rachel Dyson, Programme Manager, Anglian Water “We have been quiet as an industry on wet wipes, but now we are being vocal, because of the problems they are causing.” Read More >
- Supply Network Manager Location: Somerset Salary: £30,767 to £41,226 per annum Looking for your next career move in water supply? If so, we may have a fantastic... Read more here.
- Senior Analyst The Organisation The Water Industry Commission for Scotland is the economic regulator of the water and sewerage industry in Scotland. ... Read more here.
- Key Account Manager Key Account Manager Competitive Salary: £40,000+ DOE London and Thames Valley Knowledge, Skills & Experience Commercially astute with... Read more here.
- Contracts Manager Contracts Manager Castle Water Limited Castle Water is the leading independent water retailer in the UK, and one of the fastest growing... Read more here.
- Divisional Customer Services Director Castle Water is the leading independent water retailer in the UK, and one of the fastest growing utility supply companies, supplying services... Read more here.